During a recent home inspection we discovered moisture stains on wall and ceiling near the dryer vent. In this home the laundry room was located on the second floor. The dryer vent connection box is recessed in the wall behind the location of the clothes dryer. The vent runs vertically up the wall and continues through the attic and terminates through the roof above.
After inspecting the metal dryer duct that traveled through the attic it was determined that condensation was developing on the pipe and dripping down to the ceiling below. We recommend that the duct be inspected and cleaned out if necessary by a HVAC or duct cleaning company. If condensation continues to still be a problem the home owner should consider relocating the duct pipe with the shortest run possible to the exterior.
At B-Home Inspections we make it convenient to book and inspection with us. Our home inspection reports are easy to read. We also follow a strict Code of Ethics and Industry Standards of Best Practice. Book now to secure the best time and day for your next home inspection.